Rego 190KG Cylinder Tank Multi Valve with POL/BBQ Vapor Outlet, Bleeder, Filler
Rego 190kg Domestic Cylinder Multi Valve
This is a brand new Rego Multi Valve to suit 190KG LPG Cylinders.
It is vapor withdrawal and has an outlet connection of CGA510/POL/ BBQ fitting, the same as you would find on any 9Kg BBQ bottle .
Also has a bleeder valve ( Ullage) to aid in decanting refilling and also to determine the 80% fill limit.
It also has an Automotive style LPG filler connection 1 & 3/4" Acme.
The pressure relief is high flow to suit the 190KG Cylinders.
- Manufacturer: Rego, USA
- Model No: IND-190RG
- Pressure Relief Flow Rate: 1835 SCFM at 480 PSI
- Working Pressure: 2.55 Mpa
- Outlet: POL/BBQ/CGA510 .
- Inlet: 1 & 3/4" Acmes.
- Copper preset Dip Tube to 80% Liquid LPG Capacity for 190KG Cylinder
- Thread to tank is 3/4" NPT Male
- Length: 440mm
- Width Long Side: 150mm
- Width Short Side: 70mm
- Made in the USA
- 1 x Multi Valve
- 1 x Filler Cap
LPG is a compressed flammable liquid. Only licensed, trained and competent personal should conduct any operation or repairs relating to an LPG systems, LPG Component or LPG Storage Vessels.
Be aware of your surroundings as LPG vapour is flammable and must be kept away from all ignition sources such as pilot lights and piezo igniters in hot water systems, open flames, cigarettes, welding and grinding sparks and any other potential ignition source. Avoid direct contact with liquid LPG as a freeze burn may result. One litre of liquid LPG expands to 270 litres of combustible vapour. Personal protective equipment must be worn when working with LPG.
Cylinders are designed to only fill to 80% of the water capacity to allow for expansion of the liquid with temperature changes. This 80% level must not be exceeded when filling an LPG Cylinder. Ensure the LPG storage vessel(s) are in date and in good repair prior to filling.
Appliances intended to use vapour must not be supplied liquid LPG. Catastrophic failure may result.
Ensure all connections, seals, hoses and valves are clean, undamaged and in good repair prior to carrying out any operation. All connection must be check for leaks with a non-corrosive leak detection fluid prior to operation.
Keep all LPG Storage Vessels out of reach of Children.
Improper installations and repairs could result in serious personal injury and property damage.